Selection and Limitations of Piping Components
- Pipes and Fittings
- Comments on selection and Limitations of Components
- Piping Joints
- Fabrication, Assembly and Erection of Process Plant Piping
- Examination , Inspection and Testing
Pipe and Fittings
Comments on Selection and Limitations of Components
- Welding fittings are usually preferred to flanged fittings, not only for economic reasons but because the potential for leakage is reduced.
- Pipe bends are preferred to butt welding elbows for reciprocating compressor suction and discharge piping, vapour relief-valve discharge piping, and piping conveying corrosive fluids (such as acid where turbulence in a fitting may cause excessive corrosion).
- Bends or dead end tees should be used for piping which conveys pulverized abrasive solids suspended in gas in the dilute phase. Dead end tees (so arranged that the flow will impinge against the dead end) have a longer life than bends in abrasive service and should be used if the system can be designed to accommodate the resulting increase in pressure drop.
- Bends should be used for dense phase flow of pulverized abrasive solids and for all piping which handles either pulverized or granular solids suspended in liquids or granular solids suspended in gases.
- If the flow is through a branch into a header (or run pipe) in a piping system which transports pulverized abrasive solids suspended in gas in the dilute phase, a dead end cross (so arranged that the flow will impinge against the dead end) should be used.
- In services with very high corrosion rates, butt welding fittings with the same inside diameter (ID) as the attached pipe (if not the same, consider taper boring the component with the smaller ID) are preferred to threaded and socket welding fittings.
- Threaded cast iron fittings should not be used in pressurized process and utility piping.
- Threaded plugs are preferred to pipe caps for threaded end closures to reduce dead end corrosion problems.
- In most process plants, internal corrosion is a greater problem than external corrosion. Consequently, it is common practice that all 3/4 in and larger steel and cast iron (and all 2 1/2 in and larger brass) gate, globe, and angle valves (located above grade) be of the outside screw and yoke type.
Please note, we do not host any material and these are being shared from links found online. If anyone has objection with this, kindly email at email@example.com. Proper action shall be taken within 48 hours.